Heat pump (air conditioning) was thoroughly cleaned, refrigerant pressure checked, gas backup system was checked for fan usage and inside furnace condenser coil was inspected. Gas water heater was inspected and expansion tank was found to be defective. Homeowner will replace this unit. William did an excellent job with a careful inspection of all items. I was very satisfied with this service at a very reasonable price.